A solution to correcting false alarms involving the activation of a smoke detector can be corrected by taking a can of compressed air and dusting or "blowing out" the detector. This operation should remove the condition creating the problem but the detectors sensitivity should be tested to ensure it is still within the manufacturer's operating guidelines. In cases of repeated false alarms involving steam or vapors from cooking and baking operations heat detectors may be substituted for smoke detectors to provide protection for those areas.
Beam type smoke detectors or infrared devices activating due to obstructions, light reflections or sunlight can also be corrected by simple means. Beam smoke detectors require a beam of "light" to be projected from a sending unit to a receiving unit. If the light beam is obstructed the unit will transmit an alarm. These problems can be corrected by identifying and removing the obstruction.
Infrared detectors operate by "looking" for the varying light intensities of fire. Detector operation can be affected by sunlight and reflections. If the problem is identified as a reflection, remove the condition creating the reflection. If the condition is related to sunlight, have facility maintenance personnel shade the unit to remove the light condition. Care should be taken not to obstruct the area, process or tank being protected by either of these devices and the units should be inspected and tested to ensure they are in proper working order as soon as possible.
Sprinkler System Activations
Water flow switch activations can occur for obvious reasons such as a sprinkler system activating due to a head being damaged or not so apparent reasons such as water system fluctuations, pressure variations and fire or jockey pump operations. In any of these cases the company officer should direct facility maintenance personnel to have the problems identified and repaired immediately.
Fire department personnel should not perform these operations due to liability concerns. The company officer should require the facility to have the system inspected and/or tested immediately by personnel trained and qualified to repair fire alarm systems. Referrals to fire prevention officials should be made as soon as possible documenting and outlining the reasons for the false activations and the procedures implemented by facility personnel to lesson or correct the problem.
Following Up on Alarm System Problems
Fire prevention personnel should promptly follow-up on all referrals and ensure that the device, system, situation or environmental condition creating the problem has been properly corrected. The substitution of detection devices should only be allowed after proper research has been conducted to ensure the device is permitted by NFPA Standards and Fire Code Requirements. Documentation indicating the repairs to the facilities fire alarm system and the devices or detectors replaced should be obtained by fire prevention personnel and filed with the facilities inspection program file.
On-going false alarms and failure of facilities to properly maintain their fire alarm systems should be handled through either the issuance of citations, fines or court actions being sought against the facilities. Many municipal or county jurisdictions have implemented false alarm ordinances to "fine" facilities failing to adequately maintain their alarm systems and to recoup cost involving multiple fire department responses.
Fire alarm systems are installed in occupancies to promptly detect the presence of fire, alert building occupants in a timely manner to evacuate the premises, initiate protective devices (close fire doors) and notify the fire department to respond to the occupancy. Fire department responses to occupancies during fire alarm activations involve multiple apparatus with numerous personnel aboard. Unnecessary responses due to false alarms needlessly endanger fire department personnel and the general public. Measures taken to reduce or eliminate false alarms are essential to accomplish the fire department's mission to "Save Lives and Conserve Property".
MARK A. BROWN, a Firehouse.com Contributing Editor, serves as Fire Prevention Bureau Chief for the Concord, NC, Department of Fire & Life Safety. A 20-year veteran of the fire service, he is an appointed board member of the North Carolina Fire Marshal's Association and possesses an Associates Degree in Fire Protection and is. To read Mark's complete biography and view his archived articles, click here.