Thread: SCBA Question???
03-15-2011, 10:25 PM #1
- Join Date
- Jun 2007
- Some where in the station...
I have a question regarding the RIT /UAC adapter on a NFPA 1981 (2007 edition) SCBAs and was hoping that someone on here would be able to shed some light on this. Would there be any reason as to why a SCBA manufactured after the 2007 edition of NFPA 1981 would not complete the "Transfill operation" using the RIT/UAC and transfill hose with the universal connectors to equialize pressure from one SCBA to another SCBA in an emergency situation ONLY? Does anyone know of a check valve within the RIT / UAC adapter that would prohibt this kind of operation within a NFPA 1981 2007 edition SCBA?
If so would you be able to provide me with some info regarding this? I will also post this in the Firefighting section as well.
04-03-2011, 03:02 PM #2
Users Browsing this Thread
There are currently 1 users browsing this thread. (0 members and 1 guests)
By BC79er_OLDDELETE in forum Federal FIRE ACT Grants & FundingReplies: 24Last Post: 10-06-2007, 11:13 AM
By dmfireschool in forum Hiring & Employment DiscussionReplies: 0Last Post: 01-27-2007, 03:02 PM
By dmfireschool in forum Hiring & Employment DiscussionReplies: 6Last Post: 12-28-2006, 08:27 PM
By HFD4177 in forum Firefighters ForumReplies: 8Last Post: 09-24-2005, 03:21 PM
By gpowell in forum Firefighters ForumReplies: 11Last Post: 05-07-2005, 03:49 PM