We are just finishing up specing out a new engine tanker with a low hose bed. We hired a private firm to do some of the legal work as well as the actual spec writing. One of the spec writers is stating that it is now a NFPA requirement that you can't have a LDH intake on the drivers/ pump operators panel. He is saying nothing larger than a 2 1/2 can be taken in on the drivers pump panel. I see his point on the possibility of injury of the line breaks but I cant find anything in writing on it. Due to him saying that we piped a LDH intake/suction to the rear of the truck. Our guys want the side LDH intake but would like the truck to meet NFPA requirements. Has anybody had to deal with this recently?
Thanks for the help
+ Reply to Thread
Results 1 to 3 of 3
03-17-2014, 05:59 PM #1
- Join Date
- Mar 2014
LDH intake on the drivers side? NFPA standard?
03-17-2014, 06:44 PM #2Career Fire Captain
Volunteer Chief Officer
Never taking for granted that I'm privileged enough to have the greatest job in the world!
03-18-2014, 02:09 PM #3
- Join Date
- Oct 2013
You can't have a discharge larger than 2.5" on the pump operator's panel, not an intake.
NFPA 1901 Section 22.214.171.124
Users Browsing this Thread
There are currently 1 users browsing this thread. (0 members and 1 guests)
By LFD6132 in forum Fireground TacticsReplies: 1Last Post: 11-10-2008, 11:53 AM
By txgp17 in forum The EngineerReplies: 23Last Post: 05-10-2008, 05:06 PM
By EngCo29 in forum Apparatus InnovationReplies: 3Last Post: 06-17-2005, 10:39 AM
By TowerPower in forum Apparatus InnovationReplies: 25Last Post: 01-01-2002, 01:24 PM
By Smokeetr4 in forum The EngineerReplies: 32Last Post: 10-26-2001, 02:03 PM