Thread: help- NFPA code
03-23-2001, 04:10 PM #1BomZapFirehouse.com Guest
help- NFPA code
An industrial park wishes to modify its network against fires and requires ours on the matter opinion. In Mexico a law does not exist on the matter and we want to give ours opinion according to the norms of the NFPA.
Bomba. 2000 gpm - 100 psi
Tuberia principal de 8 "
Ramales de 3 - 6 "
Cisterna de 506 metros cubicos de agua
gabinetes de manguera 1 1/2 por bodega. 3
The industrial park account with 32 warehouses with different degrees from risk, in each warehouse to placed a SIAMESE (double female)adicional to the main SIAMESE at the beginning of the system.
modifications: The administrators of the park wish to eliminate the additional Siameses in the warehouses since they prefer to aprobechar the space for parking of vehicles.
the page WEB is www.ecopark.com.mx
tank,s for all your help.
Zapopan Jalisco Mexico
Users Browsing this Thread
There are currently 1 users browsing this thread. (0 members and 1 guests)