05-29-2003, 01:35 AM #1
Important Info-Fire Sprinkler Recall
WASHINGTON (AP) - It may become easier for people to get repair
work done on some of the 35 million fire sprinklers that were
recalled two years ago.
The Consumer Product Safety Commission and Central Sprinkler
Company of Lansdale, Pa., announced an update Wednesday to the
voluntary recall that involved sprinklers that may not work during
Terms of the original recall required that consumers use a
contractor from the company. The revision means that people now can
hire their own contractor. Reimbursement for the labor will be
subject to approval, so the federal agency advises consumers to
contact the company before calling a contractor.
The sprinklers in question have heads with O-ring seals that can
corrode or degrade over time and might keep them from turning on
during a fire.
The recalled sprinkler heads have the words "CENTRAL" or
"STAR", the letters "CSC", the letter "G" in a triangle, or a
star-shaped symbol stamped on either the metal frame or the
flower-shaped metal piece at one end of the sprinkler head.
Claims for more than 13 million sprinklers have been received,
company spokeswoman Anne Buchanan said, and about 6 million have
The company, an affiliate of Tyco Fire Products, is providing
the replacement sprinkler heads free of charge.
Also included in the recall were 167,000 sprinklers sold by Gem
Sprinkler Co. and Star Sprinkler Inc., which are also owned by
Tyco. Consumers can call 1-800-871-3492 for more information.
On the Net:
Consumer Product Safety Commission: http://www.cpsc.gov
Sprinkler replacement information:
(Copyright 2003 by The Associated Press. All Rights Reserved.)Proudly serving as the IACOJ Minister of Information & Propoganda!
Be Safe! Lookouts-Awareness-Communications-Escape Routes-Safety Zones
*Gathering Crust Since 1968*
On the web at www.section2wildfire.com
Users Browsing this Thread
There are currently 1 users browsing this thread. (0 members and 1 guests)