Thread: Hydrant outlet Q
06-12-2006, 05:18 PM #26
- Join Date
- Jul 2004
- Penn Valley, Ca
Sure, everyone does that when they don't have LDH but the original question was about running LDH off the side ports. And one LDH will get you a lot more water than 2 3" with a lot less effort expended.
06-13-2006, 01:54 AM #27
Originally Posted by BirkenVogt
- Join Date
- Jan 2004
Yeah, our is due to the fact that only half of our district has hydrants. The first due engines on the hydranted side have 4" supply while the first due on the non-hydranted side lay dual 3" supply. Thanks for all the information in this thread... especially fireh20... practical examples are just what I needed.
06-16-2006, 06:46 PM #28Originally Posted by hwoods
We have the first engine stop at the hydrant, forward lay to the fire. If we know a second engine is right behind the first one, then the second in engine drops the line to the first. Unless it is one of the few bad ones we are aware of, we always have more water than what we need from just static pressure of the hydrant. Maybe we are not using "big water" like you either....don't know.
Just curious as to how you do it, thats all. not trying to start a schitt stormJason Knecht
Township Fire Dept., Inc.
Eau Claire, WI
IACOJ - Director of Cheese and Whine
EAT CHEESE OR DIE!!
Users Browsing this Thread
There are currently 1 users browsing this thread. (0 members and 1 guests)
By Fire304 in forum Apparatus InnovationReplies: 45Last Post: 06-05-2011, 11:56 PM
By FFFRED in forum Firefighters ForumReplies: 23Last Post: 08-06-2006, 03:25 PM
By rumlfire in forum Volunteer ForumReplies: 14Last Post: 08-01-2006, 11:35 PM
By 640SATFD in forum Apparatus InnovationReplies: 12Last Post: 03-11-2003, 01:05 AM
By D Littrell in forum Apparatus InnovationReplies: 1Last Post: 09-08-2000, 07:36 PM