for sprinkler heads to be away from walls? I for whatever reason cannot find any info....I recall hearing 18 inches.
+ Reply to Thread
Results 1 to 2 of 2
Thread: What is the proper distance
10-29-2007, 02:32 PM #1
What is the proper distance"If people concentrated on the really important things in life, there'd be a shortage of fishing poles."
"Criticism is prejudice made plausible."
- H. L. Mencken (1880-1956)
10-29-2007, 06:55 PM #2
- Join Date
- Aug 2006
The minimum distance is 4". The maximum distance is the half-spacing for the head, which for standard heads is 7'-6". This distance can be extended to half the distance for extended coverage heads, however these heads must be hydraulically calculated, and in some instances the head will loose it's q-r listing. Small rooms (less than 800 sf) can have heads further off the wall.
Users Browsing this Thread
There are currently 1 users browsing this thread. (0 members and 1 guests)
By ptfd1819 in forum Fireground TacticsReplies: 16Last Post: 09-01-2006, 02:04 PM
By BVFD1983 in forum IllinoisReplies: 13Last Post: 09-28-2005, 11:20 PM
By Dishwasher in forum Hiring & Employment DiscussionReplies: 5Last Post: 08-19-2004, 10:18 PM
By OSUfirepro in forum Firefighters ForumReplies: 8Last Post: 11-16-2003, 10:15 AM
By jonesy0924 in forum Emergency Services TrainingReplies: 2Last Post: 06-07-2003, 09:09 PM